StandardsInternational : EN 50525-2-31; IEC 60227-3
Cu/PVC are insulated stranded copper conductors used for fixed protected installations indoors for power supply or lightings (from offices, domestic or commercial buildings ...) with voltage ≤ 1000V AC or ≤ 750 V DC .
Stranded bare copper class 2 to BS EN 60228.
Polyvinyl chloride "PVC"
In conduit, insulated support, ducts... in coverd and dry place.
The packing will be in coils with 91.4 m and Drums.
450/750 V Cu/PVC 1x < CSA> mm2 H07V-R EN 50525-2-31 BASEC Made In Qatar QICC - Nexans
Permissible current and voltage drop are given
For conductor laid alone in insulating tube on a wall Temperature = 30°C.
Permanent operation If conditions are different, apply correction factors from IEC 60364-5-52 standard or other equivalent national standard Voltage drop Calculated with cosj = 0,8
|Conductor flexibility||Stranded class 2|
|Conductor material||Bare copper|
|Rated Voltage Uo/U (Um)||450 / 750 V|
|Mechanical resistance to impacts||Low|
|Max. conductor temperature in service||70°C|
|Short-circuit max. conductor temperature||160°C|
|Operating temperature, range||-5 .. 60°C|
|Bending factor when installed||12(xD)|
|Bending factor when laying||6(xD)|